Jan 7, To obtain the NPAG book, by download or CD-ROM, please use the contact form Jan 7, In order to provide the modern practicing substation engineer with reference material, AREVA’s Network Protection & Automation Guide. Alstom NPAG Network Protection & Automation Guide – New still sealed. EUR ; + EUR postage. MITZ N MITZ01L1AAB ALSTOM.
|Published (Last):||12 March 2009|
|PDF File Size:||15.32 Mb|
|ePub File Size:||11.89 Mb|
|Price:||Free* [*Free Regsitration Required]|
Knowledge of the behaviour of the principal electrical system plant items under normal and fault conditions is a prerequisite for the proper application of protection. This includes a new chapter on the protection of a. Recent developments such as privatisation started to focus attention on the cost to the consumer of a loss in supply.
New chapters treat topics such as system integrity protection and remedial action schemes, phasor measurements and wide area schemes. Chapter 17 Generator and Generator-Transformer Protection The core of an electric power system is the generation.
The consequences of an occasional unwanted trip are far more acceptable the control centre simply recloses the tripped CB, some trains are delayed while the control centre ensures it nnpag safe to reclose than the consequences of a failure to trip for a fallen wire or a traction unit fault. One form of ‘Unit Protection’ is also known as ‘Differential Protection’, as the principle is to sense the difference in currents between the incoming and outgoing terminals of the unit being protected.
At the same time, reliability levels have been maintained or even npagg and availability significantly increased due to techniques not available with older relay types. Thank you for posting this greatly sought out book and articles from time to time that help us electrical engineers keep up to date.
Permanent faults, such as broken conductors, and faults on underground cable sections, must be located and repaired before the adeva can be restored. The performance of measuring transformers during and following large instantaneous changes in the input quantity is important, in that this quantity may depart from the sinusoidal waveform.
Unit protection schemes, formed by a number of relays located remotely from each other, and some distance protection schemes, require some form of communication between each location in order to achieve a unit protection function.
Many of the techniques that have been evolved for EHV power systems may be applied to lower voltage systems also, but typically on a reduced scale. The considerations for a transformer protection package vary with the application and importance of the transformer.
Overcurrent protection, on the other hand, is directed entirely to the clearance of faults, although with the settings usually adopted some measure of overload protection may be obtained.
Finally, new chapters covering the fields of power system measurements, power quality, and substation and distribution automation are found, to reflect the importance of these fields for the modern power system engineer.
eBook NPAG 2012 – Windows Application – Network Protection & Automation Guide
Chapter 16 Transformer and Transformer-Feeder Protection The considerations for a transformer protection package vary with the application and importance of the transformer. Chapter 25 Distribution System Automation Automation of distribution systems has existed for many years. Sincethe Network Protection and Automation Guide formerly the Protective Relays Application Guide has been the definitive reference textbook for protection engineers and technicians. Chapter 15 Busbar Protection The protection scheme for a power system should cover the whole system against all probable types of fault.
Shoukat Ali Jun 10, All motors need protection, but fortunately, the more fundamental problems affecting the choice of protection are independent of the type of motor and the type of load to which it is connected. These requirements can be readily expressed in mathematical logic truth tables, Boolean algebra, etc. Transient faults are commonly caused by lightning and temporary contact with foreign objects. A disturbance that affects a process control computer in a large industrial complex could easily result in shutdown of the process.
Such ‘measuring’ transformers are required to produce a scaled down replica of the input quantity to the accuracy expected for the particular measurement; this is made possible by the high efficiency of the qreva. Faults in these area are cleared in Zone 1 time by the protection at one end of the line and in Zone 2 time by the protection at the other end of the line. The problem of combining fast fault clearance with selective tripping of plant is a key aim for the protection of power systems.
Mohamed 11 Aug 09, Similarly, a protection relay affected by a disturbance through conduction or radiation from nearby conductors could trip a feeder or substation, causing loss of supply to a large number of consumers.
To reduce the effects of arva stress and electrodynamic forces, it is advisable to ensure that the protection package used minimises the time for disconnection in the event of a fault occurring within the transformer.
Such equipment can both cause and be affected by electromagnetic disturbances. This advantage is balanced by the fact that the unit scheme does not provide npsg back up protection for adjacent feeders given by a distance scheme. Unlike phase and neutral overcurrent protection, the key advantage of distance protection is that its fault coverage of the protected circuit is virtually independent of source impedance variations.
This should not be confused with ‘overload’ protection, which normally makes use of relays that operate in a time related in some degree to the thermal capability of the plant to be protected.
There are some important differences between the protection of induction motors and synchronous motors, and these are fully dealt with in the appropriate section.
Search – Schneider Electric
Existing chapters on distance, busbar and generator protection have been completely revised to take account of new developments, including improvements due to numerical protection techniques and the application problems of embedded generation.
The testing of protection equipment may be divided into four stages: Mansor Ndiaye Apr 21,