Buy ASTM D R TEST METHOD FOR LOW STRAIN IMPACT INTEGRITY TESTING OF DEEP FOUNDATIONS from SAI. ASTM D compliance statement of PET – Pile echo tester. Standard Test Method for Low-Strain Impact Integrity. Testing of Deep Foundations (ASTM D ), and. Standard Test Method for High-Strain Dynamic.
|Published (Last):||17 May 2009|
|PDF File Size:||20.17 Mb|
|ePub File Size:||14.62 Mb|
|Price:||Free* [*Free Regsitration Required]|
A superscript epsilon e indicates an editorial change since the last revision or reapproval. This data assists evaluation of pile integrity and pile physical dimensions that is, cross-sectional area, lengthcontinuity, and consistency of the pile material. Attach the appropriate motion sensor see 5.
ASTM D 5882-16 Compliance Statement
It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. These notes and footnotes excluding those in tables and figures shall not be considered as requirements of the standard. Use integrity evaluation from low strain tests together with other information, including pile installation procedures and observations, soil information, loading requirements, etc.
This standard does not purport to address all of the safety concerns, if any, associated with its use.
Consistent records are the result of uniform impacts on sound concrete, transducer systems that are properly functioning, motion sensors that are?
These data assist evaluation of the pile cross-sectional area and length, the pile integrity and continuity, as well as consistency of the pile material, although evaluation is approximate. Other useful information to consider and compare with results of this test includes low strain integrity test results of similar piles at the same site, concrete cylinder or core strength test results, automated monitoring data on equipment placing the concrete when augered piles are used, or information obtained from crosshole sonic logging Test Method D or thermal integrity profiling 5882 Methods D if available.
This standard is subject to revision at any time by the responsible technical committee and must be reviewed every? No other units of measurement are included in this standard.
ASTM D – 07 Standard Test Method for Low Strain Impact Integrity Testing of Deep Foundations
Reliable results depend on many factors; Practice D provides a means of evaluating some of those factors. Reliable results depend on many factors; Practice D provides a means of evaluating some of those factors. The method is generally not suitable for testing steel sheet, H-section or un?
The hammer must be tuned such that the fourrier transform of the measured force shall have a smooth spectrum, without any r peaks. In some cases, it may be difficult to distinguish the soil response from the pile response. Your comments are invited either for revision of this standard or for additional standards and should be addressed to ASTM Headquarters. Additional locations should be considered for piles with diameters greater than mm.
Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided satm part of the standard. Adjust the apparatus to reproduce a signal having a range of duration between 2 ms and 30 ms.
Ensure that c apparatus for recording, reducing, and displaying data is capable of determining the measurement device overload threshold. When digitizing, the sample frequency, therefore, shall be at least 30 Hz each for the motion sensor and the optional instrumented hammer, if used. Often, this method gives sufficient information for integrity evaluation.
This standard does not purport to address all of the safety concerns, if any, associated with its use. Attached to every digitized event should be identifying information names and descriptions, signal processing enhancement parameters, and date and time stamps.
For piles having minor impedance variations, the engineer should use judgement as to the acceptability of these piles 588 other factors such as load redistribution to adjacent piles, load transfer to the soil above the defect, applied safety factors, and structural load requirements. Users of this test method are cautioned that compliance with Practice D does not in itself assure reliable results.
How one applies the results obtained using this standard is beyond its scope. The accelerometer s should be placed at or near the pile head and shall have their sensitive axis parallel with the pile axis. If necessary, prepare small areas by a hand grinder to provide a smooth surface for motion sensor attachment and impact. Position the apparatus for applying the impact force so that sstm impact is applied axially with the pile and at a distance no larger than mm from the accelerometer.
The results of the analysis may include a quantitative assessment of pile integrity. The impact should be applied axially to the pile normally on the pile head. The time domain record is then evaluated for pile integrity.
The uniformity and accuracy of the digital sampling frequency is critical; the clock jitter sampling frequency astn must xstm within 0.